Open Loop Lube Oil Flushing
A Saskatchewan power producer required oil flushing on the lube oil system of their steam turbine generator.
A Saskatchewan power producer required oil flushing on the lube oil system of their steam turbine generator. This lube oil system posed a unique set of challenges to overcome. It had three bearing housings that were open to the atmosphere, which provides a significant risk of spills during oil flushing operations.
The pre-engineering for this system needed to be designed to overcome the pressure drop while still maintaining adequate velocity throughout the piping to achieve turbulent flow. Too much pressure would have caused oil to flow out of the open bearing housings on the turbine. Every loop was meticulously designed to ensure the system would surpass client cleanliness expectations without causing an oil spill.
Through the use of our specially designed oil flushing equipment, our personnel were easily able to maintain the very specific flow rate and pressure. Our all encompassing flushing equipment allows us to heat, filter, change direction of flow, and control the flow rate of the oil all from one unit.
The flushing oil was heated to 80oC and flushed at a minimum flow velocity of 3 m/s to achieve turbulent flow in all piping. Pneumatic vibrators were also used to assist in the removal of stubborn debris.
The client required cleanliness specification of ISO 4406 16/14/11 was determined using an onsite particle counter. This was achieved within 9 days of flushing.
Download a PDF Copy
More Lube Oil Flushing Service Resources
Related Case Study
Pre-Commissioning and Commissioning a Northern Alberta SAGD Facility
Service Line Page
Get more information about our lube oil flushing services.
Visit our resource library to download our lube oil flushing brochure.
Request More Information
Looking for more information on this service line? Click the button to be taken to our contact form. For additional information like brochures and case studies, visit our Resource Library